Watts 3 N 223FS-M2 Series N223FS High Capacity Water Pressure Regulator Valve - 3"
This item is no longer availableFor your convenience, we recommend:
Watts 3 LFN223FM2View this item
The Watts 3 N 223FS-M2 is a High Capacity Water Pressure Regulator Valve that can handles pressures of up to 175psi. The Watts 3 N 223FS-M2 was designed to reduce incoming water pressure and conserve water while protecting your plumbing systems.
Since 1874, the Watts Water Technologies has built upon their water technologies to provide efficient conservation of water in commercial, residential, industrial and municipal applications. In the early 1900’s, Watts introduced the revolutionary combination of temperature and pressure relief valves. This prevented hot water heaters from exploding. Today this technology continues to be a necessary part in every water heating system.
Features:• Enlarged diaphragm, spring cage and seat orifice for super capacity performance|
• Iron body construction
• Stainless steel piston
• Series N223FS furnished with separate strainer
• Optional bypass feature controls thermal expansion pressure (NOTE: The bypass feature will not prevent the pressure relief valve from opening on the hot water supply system with pressure above 150psi (10.3 bar)
• Sealed spring cage on all models for accessible outdoor or pit installations
Specifications:• Dimensions: 22 5/8" W x 14 1/2" H|
• Connection: 3 In. Flanged inlet x 3 In. Flanged outlet with strainer
• Weight: 120 Lbs
• Materials: Body: Iron coated with corrosion-resistant cold galvanizing
• Seat: Replaceable stainless steel
• Diaphragm: Reinforced Buna-N
• Disc: EPDM
• Piston: Stainless steel
Pressure Temperature:Temperature Range: 33 Degree F 160 Degree F (0.5 Degree C 71 Degree C)
• Maximum Working Pressure: 175psi (12.1 bar)
• Adjustable Reduced Pressure Range: 25 75psi (172 517 kPa)
• Standard Reduced Pressure Setting: 50psi (345 kPa)
Specifications: A Water Pressure Reducing Valve shall be installed on the water service pipe near its entrance to the building where supply main pressure exceeds 60psi (413 kPa) to reduce it to 50psi (345 kPa) or lower. Sill cocks and outside wall hydrants may be left on full main pressure at the option of the owner. Provision shall be made to permit the bypass flow of water back through the valve into the main when pressures, due to thermal expansion on the outlet side of the valve, exceed the pressure in the main supply. Pressure reducing valves with built-in bypass check valves and strainer will be acceptable.
Write Your Own Review:
Questions & Answers
If you are a new customer, please register first: